Reverse-flow Square cooling tower
Reverse flow Type square Cooling tower product model Description:
1, Design parameters:
Countercurrent Square Industrial tower: Air Wet ball temperatureΤ=28℃, Cooling tower temperature drop:10~25℃.
The Countercurrent Square civil tower is: Air wet ball temperatureΤ=28℃, Cooling tower temperature drop:5~8℃.
2, Countercurrent typeSquare Cooling TowerThe choice needs to know the amount of cooling waterQ, into the tower water temperatureT1, into the tower water temperatureT2, into the gas wet bulb temperature.
3, countercurrent square Cooling tower material can withstand-50℃ is low temperature, but for the coldest average monthly temperature is lower than10The area of ℃ should indicate the order in order to take anti-freezing measures.
4, the turbidity of circulating water is not less than50mg/L, short term not greater than100mg/LAnd should not contain oil and mechanical impurities. If necessary, anti-algae and water quality stabilization measures should be taken.
5, Countercurrent square Cooling tower in and out of the direction of the water pipe can be180Degree270Degree of rotation.
6, the water system is designed according to the nominal water flow, such as the actual amount of water and the name of the difference in ±15%Above, you should describe the order in order to modify some data.
7, Countercurrent square Cooling tower inlet temperature does not exceed60℃, if the order should be noted60℃ or more. Fan blade mounting angle adjustable, but to maintain the same angle.
The current of the motor does not exceed the rated current of the motor.
9, the fan can be reversed at short and low speed to eliminate icing.
10, the use of countercurrent square cooling tower water disk to make a pool, should be set up a separate "automatic water supply pipe", "fast water pipe", "sewage pipe", "overflow pipe", the order must be clearly stated, the cost is also included. Motors, fans are supporting the supply, the factory needs to send people to the site installation or technical guidance.